Microbiological qualificationof air, waterand dialysate in a haemodialysiscentre; a new focus on Legionella spp
Background and Objectives: The microbiological monitoring of the water used for haemodialysis is important especially for Legionella and non-fermentative bacteria since patients with end stage renal disease (ESRD) are suffering from deteriorated function of immune system.
Materials and Methods: A total 50 water and dialysate samples were weekly collected over a period of 10 weeks from 5 sites. Total and faecal coliforms were determined by utilizing the most probable number (MPN) method. For isolation of Legionella, water samples were inoculated on a BCYE medium. DNA extraction was performed and was used to amplify 16S rRNA gene of Legionella species. Airborne bacteria were sampled using a single stage Andersen air sampler.
Results: Out of total 50 water samples, 24 samples had bacterial contamination. The highest rate of Legionella contamination was observed in the storage tank (67 cfu/ml). Legionella was not isolated from the dialysate effluent samples. The highest rate of total bacterial count was related to the dialysate effluent and the maximum total count of coliforms was related to the reverse osmosis. The isolated bacteria were Gram-negative bacilli (mostly Pseudomonas isolates), Gram-positive cocci (mostly Micrococcus spp.) and Gram-positive bacilli (mostly Bacillus spp.). Six samples were contaminated with coliforms. No faecal coliform was isolated from the samples.
Conclusion: These results indicated that dialysis machine is an important source of contaminations such as Staphylococcus, Pseudomonas and Legionella. Therefore an efficient prevention program is needed to eliminate bacterial contamination of dialysis water system. Moreover, in haemodialysis centres, periodic surveillance programs for microbiological qualification can lead to a better planning for disinfection of haemodialysis water systems.
Dadgari A, Dadvar L, Eslam-Panah H. Multidimen- sional fatigue syndrome and dialysis adequacy among elderly patients under hemodialysis treatment. IJHS 2015; 1:5-8.
Ebrahimi H, Sadeghi M, Amanpour F, Dadgari A.Influence of nutritional education on hemodialysis pa- tients' knowledge and quality of life. Saudi J Kidney Dis Transpl 2016; 27:250-255.
Abbott KC, Agodoa LY. Etiology of bacterial septice- mia in chronic dialysis patients in the United States. Clin Nephrol 2001; 56:124-131.
Locatelli F, Altieri P, Andrulli S, Bolasco P, Sau G, Pedrini LA, et al. Hemofiltration and hemodiafiltration reduce intradialytic hypotension in ESRD. J Am Soc Nephrol 2010; 21:1798-1807.
Berns JS, Tokars JI. Preventing bacterial infections and antimicrobial resistance in dialysis patients. Am J Kid- ney Dis 2002; 40:886-898.
Jackson BM, Beck-Sague CM, Bland LA, Arduino MJ, Meyer L, Jarvis WR. Outbreak of pyrogenic reactions and gram-negative bacteremia in a haemodialysis cen- ter. Am J Nephrol 1994; 14:85-89.
International Organization for Standardization (IOS).Water for haemodialysis and related therapies; ISO 13959. IOS; Geneva, Switzerland Apr 15, 2009.
Ward RA. Worldwide guidelines for the preparation and quality management of dialysis fluid and their im- plementation. Blood Purif 2009; 27:2-4.
O’Neill E, Humphreys H. Surveillance of hospital wa- ter and primary prevention of nosocomial legionellosis: what is the evidence? J Hosp Infect 2005; 59:273-279.
Colbourne JS, Dennis PJ, Trew RM, Berry C, Vesey G.Legionella and public water supplies. Water Sci Tech- nol 1998; 20:5-10.
Palusińska-Szysz M, Cendrowska-Pinkosz M. Patho- genicity of the family Legionellaceae. Arch Immunol Ther Exp (Warsz) 2009; 57:279-290.
Yaslianifard S, Mobarez AM, Fatolahzadeh B, Feiz- abadi MM. Colonization of hospital water systems by Legionella pneumophila, Pseudomonas aeroginosa, and Acinetobacter in ICU wards of Tehran hospitals. Indian J Pathol Microbiol 2012; 55:352-356.
Kusnetsov J, Torvinen E, Perola O, Nousiainen T, Kati- la ML. Colonization of hospital water systems by legio- nellae, mycobacteria and other heterotrophic bacteria potentially hazardous to risk group patients. APMIS 2003; 111:546-556.
Department of environment and heritage protection, Queensland government (2009). Monitoring and sam- pling manual. Environmental protection (Water) poli- cy. Version 2, July 2013 format edits.
Sutton S. The most probable number method and its use in QC microbiology. J GXP Compliance 2010; 14:28-33.
Veronesi L, Capobianco E, Affanni P, Pizzi S, Vitali P, Tanzi ML. Legionella contamination in the water system of hospital dental settings. Acta Biomed 2007;78:117-122.
Miyamoto H, Yamamoto H, Arima K, Fujii J, Maru- ta K, Izu K, et al. Development of a new seminested PCR method for detection of Legionella species and its application to surveillance of legionellae in hospi- tal cooling tower water. Appl Environ Microbiol 1997;63:2489-2494.
Hosseini Doust R, Mohabati Mobarez A, Esmailli D.Detection of Legionella in hospital water supply using Mip based primers. J Biol Sci 2008; 8:930-934.
EudraLex (2010). “The rules governing medicinal prod- ucts in the European Union (EU)” (Vol 4), Guidelines of Good Manufacturing Practices for medicinal prod- ucts for human and veterinary use (http://ec.europa.eu/ health/documents/eudralex/vol-4/index_en.htm).
Hoenich NA, Levin R. The implications of water qual- ity in hemodialysis. Semin Dial 2003; 16:492-497.
Pisani B, Simöes M, Prandi MAG, Rocha MMM, Gonçalves CR, Vaz TMI, et al. Outbreak of Pseudo- monas aeruginosa bacteremia in a hemodialysis center in Campinas, Säo Paulo, Brazil. Rev Inst Adolfo Lutz 2000; 59:51-56.
Zunino P, Beltrán L, Zunino L, Méndez H, Percovich V, Rocca R, et al. Microbiological quality of hemodial- ysis water in a three-year multicenter study in Uruguay. J Nephrol 2000; 15:374-379.
Magalhães M, Doherty C, Govan JR, Vandamme P.Polyclonal outbreak of Burkholderia cepacia complex bacteraemia in haemodialysis patients. J Hosp Infect 2003; 54:120-123.
Arvanitidou M, Vayona A, Spanakis N, Tsakris A. Oc- currence and antimicrobial resistance of Gram-nega- tive bacteria isolated in haemodialysis water and dialy- sate of renal units: results of a Greek multicentre study. J Appl Microbiol 2003; 95:180-185.
Hrubá L. The colonization of hot water systems by Le- gionella. Ann Agric Environ Med 2009; 16:115-119.
Nunes ZG, Martins AS, Altoe AL, Nishikawa MM, Leite MO, Aguiar PF, et al. Indoor air microbiological evaluation of offices, hospitals, industries and shopping centers. Mem Inst Oswaldo Cruz 2005; 100:351-357.
Huang PY, Shi ZY, Chen CH, Den W, Huang HM, Tsai JJ. Airborne and surface-bound microbial contamina- tion in two intensive care units of a medical center in central Taiwan. Aerosol Air Qual Res 2013; 13:1060-1069.
Mirzaii M, Emaneini M, Maleknejad P, Jonaidi N, Fooladi AA, Aligholi M, et al. Distribution of bacterial contamination in a teaching hospital in Tehran-a spe- cial focus on Staphylococcus aureus. Acta Microbiol Immunol Hung 2012; 59:1-11.
Association for the advancement of medical instru- mentation (AAMI). Water treatment equipment for haemodialysis applications and related therapies. AN- SI-AAMI project RD62: 2006.
|Issue||Vol 8 No 4 (2016)|
|Microbiological qualification Haemodialysis Legionella|
|Rights and permissions|
|This work is licensed under a Creative Commons Attribution-NonCommercial 4.0 International License.|